The Refuge Call Center(s) shall be Surface Mount type and shall be heavy-duty steel in a powder coated finish, with twist lock closure. The cabinet shall be able to accept a Fireman's Lock (not provided by Alpha Communications®). The Refuge Call Center(s) shall be programmable to call out on a telephone line to a 911 call center or other emergency call locations.
These units shall be powered by a model PWRAPC power supply (up to 36 remote call boxes) or a model PWRAPC112 power supply (for 37 to 112 remote call boxes) and the power supply shall contain the built-in battery back-up and charger circuitry required for these devices.
The RCC2516CS shall be capable of connecting with up to (16) and the RCC2556CS shall be capable of connecting with up to (56) and the RCC25112CS shall be capable of connecting with up to (112) of the RCB2400 series Refuge Call Boxes
The Refuge Call Center(s), shall be IBC, NFPA and ADAAG code compliant, and shall also be Elevator Code compliant.
Contractor shall observe all local and national electrical and building codes.
The Alpha Communications® RCC2516CS (16-station), RCC2556CS (56-station) and RCC25112CS (112-station) Refuge Call Centers are used with the AlphaRefuge™ 2400 Series Area of Refuge system, and are Surface Mount type built into a lockable painted cabinet. They are used with the RCB2400 Series Refuge Call Boxes.
Only one (1) PWRAPC power supply is needed per system for up to 36 RCB2400 series refuge call boxes. For systems with 37 to 112 RCB2400 series refuge call boxes, use the PWRAPC112 power supply in place of the PWRAPC unit.