The master (main) occupant help station(s) (OHS) shall be Alpha Communications® / TekTone IR345C or approved equal. The IR345C shall include solid-state LSI/microprocessor technology, a red "CALL" indicator, a 6' long pull cord for "HELP" call placement, a routine "CALL" push button and a "CHECK-IN/RESET" push button.
All station components shall be housed in an attractive, flame retardant type ABS plastic panel. Plugin type connectors shall be used for electrical connections.
Contractor shall observe all local and national electrical and building codes.
Calling the master station is accomplished either by pulling the 6' long "HELP" cord mounted on the panel or by depressing the routine "CALL" button. Call-placed assurance is indicated by the red indicator. The speaker-microphone is sensitive enough to assure clear conversation even with weak resident/patient inputs. Calls are canceled simply by depressing the "RESET" button.
||Height: 4.50" (119mm) Width: 6.38" (162mm) Depth: 2.88" (73mm) Projects: 0.38" (9.5mm) above mounting surface
||Attractive, flame retardant type ABS Plastic (White)|
||Light texture, fog white color.
||Steel City #H3BD with Steel City #3GC plaster ring, or Alpha Communications® Part #IH353 box with IH352 ring, or EXACT EQUAL. Horizontal mount.|
||2.50" diameter, 60 ohm w/voice response|